Bahra Cables Company was established in to serve Saudi & GCC Markets. . This Catalogue is intended for Medium Voltage Power Cables, Aluminum. MEDIUM VOLTAGE POWER CABLES CONTENTS GENERAL 1 INTRODUCTION TECHNICAL 4 INFORMATION Single Core XLPE Insulated. TECHNICAL INFORMATION COPPER CONDUCTOR | STEEL TAPE ARMOURED | /15 ()kV Size mm2 25 35 50 70 95
|Published (Last):||1 June 2017|
|PDF File Size:||2.4 Mb|
|ePub File Size:||7.96 Mb|
|Price:||Free* [*Free Regsitration Required]|
Bahra Cables Factory occupies over ,square meters of prime manufacturing space together with associated design offices, laboratoriesand storage area. When the screening bonded to earth it fables also carry out theshort circuit fault current.
Axial spacing between cables Trefoil formation S: Conductor required cross sectional area. Cables to this category are complying with the requirements of BS Flat Touching A Formation Approx. Voltage between phases conductors 2. The standard sheath color is Black or Red which has a suitable UV proved additive is added to ensure resistance to cablew.
Single-core cables are suitable for d. The calculation is based on the standard dimensions of cables catzlogue on IECwhich may have a slight difference from the applied cable dimension which are following the best common manufacturing practices. System Short Circuit required.
Read the Text Version. The future product scope will be extended to Extra High Voltage cables up to kv and conductor cross sections bigger than mm2. Such tape s will bind the cores together and prevent them from opening out,acts as cablles separator between different polymers used in a cable and works as a heatbarrier between the cores and the extruded bedding. Product quality complying with the local and international standards 2. Additionally, other products described in seperate publications covers: Load current A R: Cables are often supplied in heavy cable reels and handling these reels can constitutea safety hazard.
Bahra Cables Medium Voltage Catalogue
High Performance of the product and service through cooperation between experienced staff from Germany cataloggue local experts who are aware of the local market requirements and the highest international standards of cables manufacturing.
Such protrusions into the insulation or into the semi-conducting layer increase the localized stress that may exceed the long-term breakdown strength of the insulation, so the semi-conductive layer is acting as a stress control layer. The total available stock yard for drum storage is more than 80,sqm.
Capacitance to neutral 9.
Where the cables are to be laid cztalogue any other environment, reference should be made to the cable Bahra Cables Company. For the proper function, all master data materialproperties, dimensions, etc.
Create your own flipbook. No breakdown should occur.
Bahra Cables – Downloads
A Flat Formation Approx. The basis of the standard conditions is the climate conditions of the Kingdom of Saudi Arabia, which are: Required length xatalogue cables drum schedules A A 2- Laid in free air both end bonded 0.
Lifting cable drums using crane. To facilitate the selection of the cable, systems are divided into three categories as follows. Roll in the direction shown by the arrow. If the cable is not suitable for wet applications and the underground water engrossed inside it,replacing the defected section from joint to joint is the recommend solution. The values given in the tables are for one circuit installed thermally isolated from other circuits or any other heat source.
The armour provides mechanical protection against crushing forces. Such cooperation in knowhow is invested to provide our customer with the best service and support. A layer of graphite coated is applied upon customer request.
From start up with wire drawing lines to extrusion lines, to bqhra machines up to the laboratories and the final test fields, all technical equipment is provided with the highest European standards of electronic control equipment and measuring devices which insures that the requirements of different quality standards are met. Insulated conductor diameter mmd: Physical Damage during operations.
A 2- Laid in free air both end bonded Trefoil Formation Approx. A non-hygroscopic polypropylene filler is canles between laid up cores to providea circular shape to the cable.
Metallic screen type copper tape or copper wire and area copper wire screen 4. Fire or excessive temperature at the cables location. It excludes transient voltage variations, due, for example, to lightning impulses, fault conditions and rapid connection of loads. The test voltages given above are intended for cables immediately after installation and not forcables that have been in service.
It specializes in Manufacturing cayalogue Distributing Electric Cables. The nominal system voltage U, up to 1. The core catalpgue inproduction processes, material applications and logistic procedures were provided by Germanexperts with key functions being managed by German engineers. Cable special features required, e.